how to test a 3 wire submersible well pump This is a topic that many people are looking for. militaria-agent.com is a channel providing useful information about learning, life, digital marketing and online courses …. it will help you have an overview and solid multi-faceted knowledge . Today, militaria-agent.com would like to introduce to you Quảng cáo này dựa trên:. Following along are instructions in the video below:
To the goulds water technology video training series in this episode. Were going going to talk to you about using your ohm meter to troubleshoot submersible motors music make sure there is no power to the motor ohmmeters are designed to measure resistance in ohms and do so without power applied all meters may be analog or digital analog. Ohm meters such as the simpson 372 have an adjustable scale.
Which must be set prior to taking the measurement in addition they may contain a dial to zero out the meter digital meters. Such as the fluke 1587 have auto ranging features therefore. There is no need to manually adjust the scale prior to the measurement.
The fluke 1587 does not allow the meter to be zeroed out to measure line to line resistance first determine.
The motor model number. If you dont have the model number you can look it up by the voltage horsepower phase and wire configuration next look at the line to line resistance specification of the motor in ohms. Using the made manual or the pocket service manual.
Again ensure. There is no power to the motor first measure. The resistance of each line to line compare the actual value to specified values use the pocket service manual to determine what your results mean if all own values are normal.
The motor windings are neither shorted nor open and the cable colors are correct.
If any one value is less than normal. The motor is shorted if anyone on value is greater than normal. The winding or the cable is opened or there is a poor cable joint or connection.
If some own values are greater than normal. And some less the leads are mixed be sure to add resistance of your drop cable. When checking the pump in the will see the cable resistance table in the pocket service manual for reference to measure line to ground resistance with a basic digital ohmmeter.
There is no power to the motor measure. The resistance between each of the leads to ground this meter will show. Oh l.
Or open lead. If the motor has no connection between the power lead and to ground. This is a good motor.
A bad motor will show a very small resistance value between the power leads and ground to measure line to ground resistance with a digital insulation resistance meter or megger again ensure there is no power to the motor first set the appropriate dc voltage on your meter use five hundred volts dc for our goals water technology products then measure the resistance between each of the leads to ground compare the actual measurements to the normal ohm and megohm values chart in the pocket service manual. And determine the meaning of the results music. .
Thank you for watching all the articles on the topic Quảng cáo này dựa trên:. All shares of militaria-agent.com are very good. We hope you are satisfied with the article. For any questions, please leave a comment below. Hopefully you guys support our website even more.